This is the fifth edition of CSA B214, Installation code for hydronic heating systems. It supersedes the previous editions, published in 2016, 2012, 2007, and 2001.
The main changes from the previous edition are as follows:
a) added requirements for use of potable water as a hydronic fluid (Clause 22.214.171.124);
b) clarified recycling requirements for prevention of stagnation (Clause 126.96.36.199);
c) added requirement for pipe insulation in unconditioned spaces (Clause 8.2);
d) removed allowance for PVC pipes and tubing, and PVC fittings;
e) clarified that metal/plastic pipes refer to PEX-AL-PEX and PERT-AL-PERT composite pipes (Clauses 9.2.3 and 9.2.4);
f) clarified that polypropylene random copolymer refers to PP-R & PP-RCT pipes and tubing (Clauses 9.2.5);
g) added requirements for flexible pre-insulated plastic piping and installation of non-metallic piping in return air plenums (Clauses 9.2.7 and 9.2.8);
h) added requirements for support of larger sizes PEX and PERT tubing as per ASTM F876 (Clause 9.4.1);
i) added requirements for support of non-metallic pipe and tubing in support channels, and vertical run support for non-metallic pipe and tubing in support channels (Clauses 9.4.2 and 9.4.7);
j) added requirements for pipe insulation, pipe sleeves, thermal expansion and contraction, and contact with building materials (Clauses 9.5 to 9.8);
k) added requirements for PERT-AL-PERT composite pipe fittings, and plastic-to-metal connections (Clauses 10.4 and 10.10);
l) removed restriction on use for compression valves for isolation purposes;
m) added requirements for manifolds (Clause 11.3);
n) changed high-temperature requirement limit for radiant floor heating panels (Clause 12.2.2);
o) clarified requirements for makeup supply connection (Clause 12.5.4);
p) added exception for differential pressure regulation (Clause 188.8.131.52);
q) clarified requirements for air space above insulation (Clause 184.108.40.206);
r) added space limits for air space behind insulation (Clause 14.6.2);
s) added requirements for types of tube fasteners (Clause 17.4.2); and
t) added requirements for heat exchanger and piping and materials (Clause 18.4.1).
This Code has been developed in compliance with Standards Council of Canada requirements for National Standards of Canada. It has been published as a National Standard of Canada by CSA Group.
This Code sets out the minimum provisions for the installation, extension, alteration, and renewal of hydronic heating systems.
This Code applies to open and closed hydronic heating systems. These systems include
a) hydronic space heating;
b) radiant heating (wall, floor, and ceiling);
d) fan coils;
e) combination potable-water-heating and space-heating (combo) systems;
f) integrated mechanical systems;
g) indirect-fired domestic-water heating;
h) pool and spa heating;
i) snow and ice melt systems; and
j) other auxiliary systems.
1.3 Interchangeable terms
The terms pipe and piping, as well as tube and tubing, are used interchangeably in this Code, unless otherwise stated.
In this Code, shall is used to express a requirement, i.e., a provision that the user is obliged to satisfy in order to comply with the Code; should is used to express a recommendation or that which is advised but not required; and may is used to express an option or that which is permissible within the limits of the Code.
Notes accompanying clauses do not include requirements or alternative requirements; the purpose of a note accompanying a clause is to separate from the text explanatory or informative material.
Notes to tables and figures are considered part of the table or figure and may be written as requirements.
Annexes are designated normative (mandatory) or informative (non-mandatory) to define their application.
1.5 Units of measure
The values given in SI units are the units of record for the purposes of this Code. The values given in parentheses are for information and comparison only.
Installation code for hydronic heating systems
Installation code for hydronic heating systems
Installation Code for Hydronic Heating Systems
An update to this product is available.
To receive notifications when an amendment, new edition or update is available to your standard no matter how you purchased it, please register on the Standards Update Service. After registering, enter the List ID for the relevant standard. The List ID can be found in the “CSA Standards Update” section within the first few pages of the standard you’ve purchased. Once notified, you can then update your standard accordingly.
PDF Format Purchased from the CSA Store
If you have purchased or subscribed to a standard from the CSA Store in PDF format, login to your CSA OnDemandTM account to access the updated PDF.
Paper Format Purchased or Purchased from Reseller
If you have purchased a paper copy of the standard from the CSA Store or purchased a standard in paper or PDF format from one of our resellers, login to the Standards Update Service to download the updates in PDF format.
eBook Format Purchased
If you have purchased a standard in eBook format, login to the CSA Reader App to download the updated version of the standard.