Codes & Standards - Purchase
Lever operated non-lubricated gas shut-off valves
This is the fourth edition of CSA 3.16, Lever operated non-lubricated gas shut-off valves. It supersedes the previous editions published in 2015, 1988, and 1985.
The major changes to this edition include the following:
a) an alternative manufacturing production test has been added; and
b) updated formatting throughout the Standard.
This Standard has been developed in compliance with Standards Council of Canada requirements for National Standards of Canada. It has been published as a National Standard of Canada by CSA Group.
This Standard applies to manual lever operated, gas shut-off valves sizes NPS 1/4 to 8 of metallic construction with weld and flanged and threaded ends other than pressure lubricated designs for use with natural gas, manufactured gas, and liquefied petroleum gases.
1) Valves covered by this Standard may be used on digester gas (methane produced during sewage treatment) but because of entrained contaminants their use is subject to agreement between the manufacturer and the purchaser.
2) Valves covered by this Standard may not be used on sour gas (gas with entrained hydrogen sulphide) without modification(s). Manufacturers should be consulted for their recommendation.
All valves covered by this Standard will be limited as to the service temperature and/or special provisions in accordance with the following designations and descriptions in Clauses 5 to 9.
a) Clause 5: –30 to 65 °C (–22 to 149 °F);
b) Clause 6: –40 to 65 °C (–40 to 149 °F);
c) Clause 7: –60 to 65 °C (–76 to 149 °F);
d) Clause 8: –30 to 120 °C (–22 to 248 °F); and
e) Clause 9: –30 to 180 °C (–22 to 356 °F).
This Standard applies to manual lever operated gas shut-off valves having maximum operating pressure over a range of 0 to 860 kPa (125 psig) and able to withstand field pressure testing to a maximum permissible pressure of 1290 kPa (187 psig).
All references to psi (kPa) throughout this Standard are considered as gauge pressure unless otherwise specified.
In this Standard, shall is used to express a requirement, i.e., a provision that the user shall satisfy in order to comply with the Standard; should is used to express a recommendation or that which is advised but not required; and may is used to express an option or that which is permissible within the limits of the Standard.
Notes accompanying clauses do not include requirements or alternative requirements; the purpose of a note accompanying a clause is to separate from the text explanatory or informative material.
Notes to tables and figures are considered part of the table or figure and may be written as requirements.
Annexes are designated normative (mandatory) or informative (non-mandatory) to define their application.
The values given in SI units are the units of record for the purposes of this Standard. The values given in parentheses are for information and comparison only.
An update to this product is available.
To receive notifications when an amendment, new edition or update is available to your standard no matter how you purchased it, please register on the Standards Update Service. After registering, enter the List ID for the relevant standard. The List ID can be found in the “CSA Standards Update” section within the first few pages of the standard you’ve purchased. Once notified, you can then update your standard accordingly.
PDF Format Purchased from the CSA Store
If you have purchased or subscribed to a standard from the CSA Store in PDF format, login to your CSA OnDemandTM account to access the updated PDF.
Paper Format Purchased or Purchased from Reseller
If you have purchased a paper copy of the standard from the CSA Store or purchased a standard in paper or PDF format from one of our resellers, login to the Standards Update Service to download the updates in PDF format.
eBook Format Purchased
If you have purchased a standard in eBook format, login to the CSA Reader App to download the updated version of the standard.