This standard applies to newly produced combination gas controls (see Definitions, Part IV), hereinafter referred to as controls, constructed entirely of new, unused parts and materials.
The combination control may include other functions such as pilot gas filters, pressure switches, etc., which shall be of an approved type (see Definitions, Part IV), or shall be investigated as an integral part of the combination control for construction and performance equivalent to an approved type.
Compliance of a combination control with this standard does not imply that the combination control is acceptable for use on gas appliances without supplemental tests with the combination control applied to the particular appliance design.
This standard applies to combination controls having a maximum operating gas pressure of 1/2 psi (3.45 kPa) with one or more of the following fuel gases: natural, manufactured, mixed, liquefied petroleum and liquefied petroleum gas-air mixtures.
This standard applies to combination controls which are capable of operation in ambient temperatures of 32°F (0°C) to 125°F (51.5°C), unless a higher temperature, lower temperature or both, are specified by the manufacturer.
Exhibit A contains items unique to the U.S.
Exhibit B contains items unique to Canada.
Exhibit C contains a list of standards specifically referenced in this standard, and sources from which these reference standards may be obtained.
If a value for measurement as given in this standard is followed by an equivalent value in other units, the first stated value is to be regarded as the specification.
All references to psi throughout this standard are to be considered gage pressure unless otherwise specified.