Motor control centres (Trinational standard with UL 845 and NMX-J-353-ANCE-2021)
This is the harmonized ANCE, CSA Group, and UL standard for Motor Control Centers. It is the third edition of NMX-J-353-ANCE, the second edition of CSA C22.2 No. 254, and the sixth edition of UL 845. This edition of NMX-J-353-ANCE/CSA C22.2 No. 254/UL 845 supersedes the previous edition published on August 31, 2005.
This standard has been developed in compliance with Standards Council of Canada requirements for National Standards of Canada. It has been published as a National Standard of Canada by CSA Group.
1.1 Products covered
This standard applies to motor control centers to be used in accordance with the U. S. National Electrical Code, ANSI/NFPA 70, CSA C22.1, Canadian Electrical Code, Part 1, and the Mexican Electrical Installations (Utility), NOM-001-SEDE.
These requirements cover motor control centers for use on circuits having available short-circuit currents not more than 200 000 A rms symmetrical or 200 000 A dc.
This standard applies to single- and three-phase 50 and 60 Hz and dc motor control centers rated not more than 1000 V ac or dc.
Requirements for fire pump controllers are as provided in Annex,
1.2 Products not covered
These requirements do not cover switchboards or panelboards intended for the control of electric light and power circuits, nor do they cover an individual unit for this purpose. Such units, however, that consist of manually or automatically operated switches, branch-circuit or service-circuit circuit-breakers, overcurrent-protective devices, or the like may be used within a motor control center.
A motor control center can contain, but is not limited to, any combination of equipment such as the following:
a) full-voltage reversing or non-reversing combination motor control units;
b) full-voltage multispeed combination motor control units;
c) reduced-voltage part-winding, wye-delta or auto-transformer combination motor control units;
d) solid-state industrial controllers, such as adjustable-speed drives, programmable controllers, protective relays, and the like;
e) lighting or distribution panelboards;
f) feeder-tap units;
g) incoming-line equipment, such as main lugs, fusible switch, isolation switch, or circuit-breaker;
h) control or lighting transformers;
i) special equipment assemblies;
j) combination contactor units.
The foregoing equipment can contain, but is not limited to, such items as pushbuttons, selector switches, indicating lights, control transformers, control circuit fuses, and auxiliary devices incorporated as an integral part of the units.
1.4 Units of measurement
The first values given are SI (metric) units. Alternate measurements shown in parentheses are US customary units, which sometimes are not strict conversions.
An update to this product is available.
To receive notifications when an amendment, new edition or update is available to your standard no matter how you purchased it, please register on the Standards Update Service. After registering, enter the List ID for the relevant standard. The List ID can be found in the “CSA Standards Update” section within the first few pages of the standard you’ve purchased. Once notified, you can then update your standard accordingly.
PDF Format Purchased from the CSA Store
If you have purchased or subscribed to a standard from the CSA Store in PDF format, login to your CSA OnDemandTM account to access the updated PDF.
Paper Format Purchased or Purchased from Reseller
If you have purchased a paper copy of the standard from the CSA Store or purchased a standard in paper or PDF format from one of our resellers, login to the Standards Update Service to download the updates in PDF format.
eBook Format Purchased
If you have purchased a standard in eBook format, login to the CSA Reader App to download the updated version of the standard.