Codes & Standards - Subscribe
ANSI Z21.101-2018/CSA 8.5-2018
This is the second edition of ANSI Z21.101 • CSA 8.5, Gas hose connectors for portable and moveable gas appliances. It supersedes the previous edition published in 2012.
This Standard applies to newly produced gas hose connectors for portable and moveable gas appliances constructed entirely of new, unused parts and materials, consisting of flexible tubing for gas leak resistance that:
a) when used indoors, hose connectors are to be equipped with a male plug fitting, which complies with ANSI Z21.90 • CSA 6.24, Gas Convenience Outlets and Optional Enclosures;
b) are for use with indoor/outdoor gas-fired appliances;
c) are for use on piping systems having fuel gas pressure not in excess of 5 psi (34.5 kPa);
d) are capable of operation at temperatures between -40°F (-40 °C) and 300° F (149 °C);
e) are of 1/4 in to 1-1/2 in nominal internal diameters;
f) are of not more than 6 ft (1.83 m) nominal length for indoor use;
g) are of not more than 15 ft (4.57 m) nominal length for outdoor use;
h) are equipped with standard taper pipe threads (conforming to the Standard for Pipe Threads, General Purpose (Inch), ASME B1.20.1 or the Standard for Dryseal Pipe Threads (Inch), ASME B1.20.3) on the end fittings attaching to the appliance and to the gas supply piping.
Connectors complying with this Standard are considered suitable for use with natural, manufactured, mixed, and LP-gas air mixtures.
If a value for measurement as given in this Standard is followed by an equivalent value in other units, the first stated value is to be regarded as the specification.
All references to psi throughout this Standard are to be considered gauge pressure unless otherwise specified.
Annex A, Items Unique to Canada, contains provisions that are unique to Canada.
Clause 2, Reference publications, contains a list of standards specifically referenced in this Standard and sources from which these reference standards may be obtained.
This Standard contains SI (Metric) equivalents to the yard/pound quantities, the purpose being to allow the Standard to be used in SI (Metric) units. (IEEE/ASTM SI 10, American National Standard for Metric Practice, or ISO 80000-1:2009, Quantities and units – Part 1: General is used as a guide in making metric conversion from yard/pound quantities.) If a value for a measurement and a corresponding value in other units are stated, the first stated value is to be regarded as the requirement. The given corresponding value may be approximate. If a value for a measurement and a corresponding value in other units are both specified as a quoted marking requirement, the first stated unit, or both are to be provided.
In this Standard, shall is used to express a requirement, i.e., a provision that the user is obliged to satisfy in order to comply with the standard; should is used to express a recommendation or that which is advised but not required; and may is used to express an option or that which is permissible within the limits of the standard.
Notes accompanying clauses do not include requirements or alternative requirements; the purpose of a note accompanying a clause is to separate from the text explanatory or informative material.
Notes to tables and figures are considered part of the table or figure and may be written as requirements.
Annexes are designated normative (mandatory) or informative (non-mandatory) to define their application.